Hot Water System in Richmond
The team at Gallant Plumbing were called out to a hot water system in Richmond. Our Melbourne plumbers attended site in a timely manner ready to rectify the clients issue.
Once arriving on site in Richmond, our hot water plumber found that the pilot light had gone out. After relighting the pilot light, the plumber tested the unit and found it stayed lit, all running as normal. Upon further inspection, the hot water system was found to have two leaking pressure and temperature released (PTR) valves. These leaky valves were likely to be causing the hot water system issues, therefore our plumber replaced both PTR valves.
Hot Water System in Richmond.
The Richmond clients hot water system also had two faulty ball valves which were not shutting off on the system. Our Melbourne plumber also replaced the two ball valves and then proceeded to purge the system. After cleaning out the system, our best plumber tested the system and found it all running as designed to and the pilot light stayed lit.
Once works were completed, the plumber spent time explaining to the client what the hot water systems issues were. He explained what he did to the unit and why, whilst also recommending further works to help prolong the life of the unit. For this specific client, the plumber recommended replacing both flues on the system due to their poor conditions.
Need a Plumber in Melbourne Now?
Do you also need a hot water plumber in Richmond? Or do you have a gas leak? A blocked drain? Or a broken gas cooktop that needs fixing? Whatever the plumbing issue is and wherever you are in Melbourne, our friendly and expert plumbers at Gallant Plumbing are the best plumbers in Melbourne and are always happy to help. Contact our reliable plumbers for a quote today!