Hot Water Service in Melbourne CBD
Gallant Plumbing were recently called out to a hot water service in Melbourne CBD. We sent out our best Melbourne plumber to fix the problem.
Firstly, our Melbourne plumber met with the client to go over the issues with the hot water.
Upon investigation, our best plumber found the hot water was not hot enough. Boosters 17, 19 and 20 were only functional on the north side and boosters 1, 14 and 15 were only functional on the south side. As a result, our plumber picked up 15 new cold water inlet filters from suppliers.
Our best Melbourne plumber began removing all 30 cold water filters from boosters, fitted 15 new filters on the North bank and cleaned all other filters and fitted the best ones in the south bank. Following on, he flushed all boosters and checked operations and building temperature.
Continuing on, our Melbourne plumber removed the cover on booster 4 and inspected it, finding the combustion fan dirty. On top of this, our best plumber found a damaged cold water expansion valve, and as a result, removed the damaged section, repaired it, and reinstated for testing.
To finish up, our plumber cleaned up and removed all associated rubbish on the site. The filters that were spare were left with the client, and our best Melbourne plumber provided the following recommendations.
- A thorough servicing of all 30 hot water boosters
- Replace any associated faulty parts
NEED A PLUMBER IN MELBOURNE NOW?
Do you also need a hot water plumber in Melbourne CBD? Or do you have a gas leak? A blocked drain? Or a broken gas cooktop that needs fixing? Whatever the plumbing issue is and wherever you are in Melbourne, our friendly and expert plumbers at Gallant Plumbing are the best plumbers in Melbourne and are always happy to help. Contact our reliable plumbers for a quote today!