Gas Leak in Forest Hill
Gallant Plumbing were recently called out to a gas leak in Forest Hill. We sent our best Melbourne plumber to solve the issue.
Our best plumber attended the site, and met with the client to discuss the issue. The client informed our plumber that a new gas line was installed in the road.
Technicians have tagged out the gas meter after a leak was evident. Firstly, our Melbourne plumber located the leak on the galvanised riser. The galvanised pipe was feeding the nearby ducted heater. As a result, our best Melbourne plumber opted to replace galvanised line with copper and run surface.
Forest Hill Gas Leak
Following this, our plumber pressure tested the line after 7kpa, pressure tested appliances at 2kpa, and reconnected the gas meter and soap tested. Everything is now working.
Finally, our best plumber relit the gas hot water system and ducted heater. As a result, the gas hot water and ducted heater are working. To finish off, our Melbourne plumber cleaned up the area, and spoke to the client about the completed job.
DO YOU NEED GAS WORKS COMPLETED?