Doncaster Gas Works
The team at Gallant were called out to attend some gas works in Doncaster. The client needed a leak to be fixed.
Our Melbourne plumber met with the client onsite who explained the problem. Firstly, the plumber made sure all 3 appliances had their gas valves turned off before commencing any tests. After the tests occurred, our plumber noticed the main line had dropped sharply. As a result our plumber began bubble testing any exposed joints. A major leak was identified on a brass barrel nut, consequently materials were sourced and the section was replaced.
Gas Works in Doncaster
Our Melbourne plumber installed a new gas regulator and gas valve inside the clients cabinet for the hot plates to bring it all up to regulation. Once again, the line was tested and there was still a small leak with the compression nut on the gas valve for the ducted heater.
Our plumber tightened the join and re tested the line. It all held at 7kpa for over 5 minutes. On top of this, the plumber opened the gas valves and tested the appliances at 1.75kpa and this also passed. To sum up, our plumber explained that all appliances have been commissioned and the gas is now fixed, including the faulty regulator.
Need a Gas Plumber in Melbourne now?
Do you also need help with a gas works in Doncaster? Or do you need a hot water plumber? Have a blocked drain? Or a broken gas cooktop that needs fixing? Whatever the plumbing issue is and wherever you are in Melbourne, our friendly and expert plumbers at Gallant Plumbing are the best plumbers in Melbourne and are always happy to help. Contact our reliable plumbers for a quote today!